By Pump UseBy Brand
TSW 32/11 A is basement drainage pump, water-cooled.
Wilo-Drain TSW 32/11 A has a turbulator that prevents the build-up of sediment, expelling it together with the fluid. This reduces costs and the time needed for regular cleaning of the sump. In addition, problems associated with mud removal and the observance of occupational safety hygiene regulations during cleaning of the pump sump are minimised.
|TS||T = submersible pump
S = wastewater
|W||W = with turbulator|
|32||Nominal diameter of pressure connection|
|/11||Max. delivery head [m]|
|A||With float switch|
Submersible pump suitable for stationary, fully automatic operation. A pressure hose of appropriate length is connected for mobile use, while a pipe is connected to the discharge port for stationary applications.
A residual current device for a trigger current of 30 mA that is to be provided on site (regulation concerning outdoor installation) must be utilised in accordance with EN 60335-2,41.
Due to its design, the TSW ensures constant turbulence in the suction area of the pump. This results in a clean pump sump.
No fluid-related odours are generated, due to the turbulence and the elimination of the settling sediment connected with it. The maintenance intervals are extended.
Jacket-cooled, stainless steel-encapsulated, dry electric motor with built-in thermal overload protection and automatic reactivation. The capacitor is on the inside.
In accordance with DIN EN 60335-2-41, 10 m of electrical connection line is required for outdoor operation (however note that regulations vary from country to country).
High operational reliability due to shaft sealing consisting of a mechanical seal on the pump side and a rotary shaft seal on the motor side as well as upstream dirt deflector for additional protection of the mechanical seal, oil barrier chamber.
Scope of delivery
Pump ready for connection with 10m cable, plug and attached float switch, supplied non-return valve and hose connector (Ø 32 mm, R1), installation and operating instructions.
Below are related articles that you may find helpful.How to Read a Pump Curve (Blog Article)