By Pump UseBy Brand
Sewage lifting unit for drainage of residential housing and commercial buildings (e.g. restaurants, department stores, etc.). Raw sewage that cannot be piped to the sewer system through the use of natural inclines and sewage from toilet systems below the backflow level are to be piped to the public sewer system by means of an automatic lifting unit in accordance with DIN EN 12056/ DIN 1986‐100. Sewage containing mineral oils or explosive admixtures must be guided through oil precipitators and/or petrol precipitators; those containing fatty substances must go through grease traps and those with sand through grit chambers. In cases where the flow to the lifting unit must not be interrupted during normal operation, one lifting unit must be equipped with a second pumping unit that has the same performance capacity and switches on automatically when needed (DIN EN 12050‐1 A1).
Fully submersible sewage lifting unit, ready for connection (flooding height: 2 mWS, overflow time: 7 days) with a gas and watertight collection tank equipped with buoyancy safeguards. Centrifugal pump with vortex impeller.
Single-pump system with single-phase or three-phase AC motor for automatic operation. Switchgear with shock-proof or CEE plug, potential-free contact, integrated alarm (mains-independent, due to built-in rechargeable battery*) and adjustable follow-up time.
RV version with non-return valve included in the scope of delivery.
Below are related articles that you may find helpful.How to Read a Pump Curve (Blog Article)